|A combined intumescent medium temperature smoke and fire seal which is heat activated. It is unobtrusively set into a machined groove around the perimeter of|
timber frames and door edges. The RP63 can be checked out in the latch area to allow for the continuation of the fin.
An effective medium temperature smoke seal is achieved with a pair of silicon fins between the door and frame.
Location: Morticed into the door frame and around stiles and head.
Min/Max Gap: 3mm to 4mm.
Finish: Satin clear (silver) anodised aluminium (15µm). Trim available in antique white.
Fixing: Adhesive fix into a 30mm x 7mm groove.
Seal: RP371Si. Grey silicon rubber (SE) with intumescent infill.
Sizes: 2400mm, 2100mm.
Fire AUS/NZ: NCC Spec. C3.4. AS1530.4 & AS/NZS 1905.1. NZ BC Compliance Doc. C/AS1 6.19.2 & App. C6.1.1.
UK/EU: Approved Document B. (Tests above are similar to BS EN 1634-1 & BS 476 Pt. 20 & 22).
FRL & FRR-/180/30 and FD180.
Smoke NCC Spec. C3.4. AS1530.7 & BS EN 1634-3. Meets smoke leakage rates specified in AS6905 & EN 13501-2 “Sa”, “Sm”.
Energy NCC Pt. 126.96.36.199 & J3.4.