Smoke Door Sealing Systems
Tested and Certified on Solid Core Doors
Effective combinations of smoke and acoustic seals tested on solid core doors that meet the requirements for AUS NCC specification C3.4 Deemed-to-Satisfy for smoke doors, UK Approved Document B and NZ Building Code Compliance Document C/AS1 Pt. 6.19.2 (b). These systems meet the leakage rates specified in AS 6905 when the door assembly is installed to AUS NCC specification C3.4 Deemed-to-Satisfy for smoke doors. Meets leakage rates specified in BS EN 13501-2 “Sa”, “Sm” classification.
Pairs of Doors
These systems have been smoke leakage performance tested to:
AS 1530.7 ≤ 40m3/h @ 25 Pa when exposed to 200°C > 30 minutes in accordance with AS 6905.
EN 1634-3 ≤ 3m3/h/m @ 25 Pa for ambient and ≤ 30m3/h @ 50 Pa for medium temperature in accordance with BS EN 13501-2.
Ⓒ Raven Products 2021
DOOR FRAME / PERIMETER SEAL
DOOR BOTTOM SEAL
THRESHOLD PLATE SEAL