Smoke Door Sealing Systems
Fire Engineered - Performance Solutions
These systems may be used where the source of exposure could be from either side of the door opening and can be used where a fire engineered solution may be required. Effective combinations of smoke and acoustic seals tested on solid core doors that meet the requirements for AUS NCC specification C3.4 Deemed-to-Satisfy for smoke doors, UK Approved Document B and NZ Building Code Compliance Document C/AS1 Pt. 6.19.2 (b). Tested to AS 1530.7 and EN 1634-3. All systems open towards positive pressure (fire side).
Smoke Leakage Rates
AS1530.7 ≤ 25m3/h @ 25 Pa for single doors and ≤ 40m3/h @ 25 Pa for double doors when exposed to 200°C for 30 minutes in accordance with AS6905.
EN1634-3 Sa; ≤ 3m3/h/m @ 25 Pa excluding the threshold for ambient. For Sm; ≤ 20m3/h @ 50 Pa for single doors and ≤ 30m3/h @ ambient and 200°C in accordance with BS EN 13501-2.
Raven conducted the successful tests shown at a NATA – ILAC certified testing Laboratory
Ⓒ Raven Products 2023
DOOR FRAME / PERIMETER SEAL
DOOR BOTTOM SEAL
THRESHOLD PLATE SEAL